Do you own or operate aboveground petroleum storage tanks in Utah? If so, then a new regulation could affect your facility whether or not that facility is regulated by Spill Prevention, Control, and Countermeasure (SPCC) rules according to the Federal Oil Pollution Prevention regulation 40 CFR part 112. The Utah Department of Environmental Quality (DEQ), Division of Environmental Response and Remediation (DERR) has begun regulating Aboveground Petroleum Storage Tanks (APSTs) as of July 1, 2021.
APSTs that are now regulated by Underground Storage Tank (UST) rules include all petroleum storage tanks greater than 500 gallons which meet one or both of the following criteria:
- The APST rests directly on soil or gravel
- Any portion of the piping associated with the tank is underground or touching soil/gravel
Therefore, you could have oil storage capacity at your facility below the SPCC threshold of 1,320 gallons but operate 550-gallon tanks and still be regulated under the Utah APST rule, even though your facility is exempt from SPCC regulation. Examples of APST regulated tanks and piping are shown below.
APSTs which are not regulated by DERR UST rules include:
- Tanks less than 501 gallons
- Tanks at commercial airports used for fueling
- Tanks used in farm or agriculture
- Tanks at petroleum distributor or refiner (SIC Code 2911 or 5171)
- Tanks related to oil or gas production and gathering operations
- Tanks used for heating oil on premises
Owners and Operators with regulated APSTs must notify the DERR by July 1, 2022.
Utah UST requirements stipulate that owners and operators of regulated APSTs must demonstrate financial responsibility to show they can pay the costs of cleanups and third-party claims for leaks from APSTs. A method of financial responsibility must be in place by July 1, 2023. The tank owner must indicate on the notification form the method of financial responsibility which is to provide this assurance.
Also, beginning May 5, 2021, all APSTs that are now regulated by DERR will be required to submit plans to the DERR for any tank closures, upgrades, line replacement, etc. And releases from regulated APSTs will now be regulated by the DERR’s Underground Storage Tank reporting requirements and cleanup standards.
The DERR’s UST reporting and clean up requirements include:
- Pay any applicable fees
- Obtain a Certificate of Compliance
- Maintain compliance with regulations
- Upgrade USTs when required
- Report any UST release to the DERR
- Remediate contamination
- Remove UST appropriately
Based on these new regulated APST requirements, it may be beneficial for APST owners/operators to modify tanks and tank piping systems to remove those tanks from APST registration and regulation.
These tank modification options could include:
- Place APST on a concrete pad or impermeable liner
- Elevate the APST to provide separation between the tank bottom and ground
- Place APST within a steel dike/containment basin
- Replace buried piping with aboveground piping
- Place impermeable material between the piping and ground
Antea Group’s tank management consultants can assist you in determining whether your APSTs are regulated under this new rule. If so, Antea Group can assist with completion and submission of the required APST Notification Form. We can also recommend modification methods should you choose to upgrade tanks and piping systems to remain exempt from the new APST rule. Get in contact with our team and find out more info on our SPCC service page below.Spill Prevention, Control, and Countermeasure (SPCC) Plans
Want more news and insights like this?
Sign up for our monthly e-newsletter, The New Leaf. Our goal is to keep you updated, educated, and even a bit entertained as it relates to all things EHS and sustainability.Get e-Newsletter